Warranty Claim Dixell products Dixell Controllers and Systems are able to give a right answer to any needs in refrigeration and conditioning applications: Industrial refrigeration: industrial refrigeration requires the control of many different conditions to guarantee that products are processed and stored correctly. The concepts of integration, remote access, energy savings and functional aesthetics are important considerations in this key field of refrigeration. Food service and cooking: Dixell is equally competent in the field of cooking, just as it is in the field of refrigeration or blast chiller processes used in freshly-cooked food conservation. Air-conditioning: The comfort of the environment in which we live nowadays is an essential element of our everyday life, and air conditioning is a decisive factor in this situation. Unlike the past, it is no longer a luxury, and it has become a necessity.
|Published (Last):||3 February 2019|
|PDF File Size:||7.77 Mb|
|ePub File Size:||5.71 Mb|
|Price:||Free* [*Free Regsitration Required]|
The regulation is performed according to the temperature measured by the thermostat probe with a positive differential from the set point: if the temperature increases and reaches set point plus differential the compressor is started and then turned off when the temperature reaches the set point value again.
In case of fault in the thermostat probe the start and stop of the compressor are timed through parameters Con and CoF. The relay of the second compressor is activated in parallel with the relay of the first compressor, with a possible delay set in the AC1 parameter. Both the compressors are switched off at the same time. The cycle can be terminated before the end of the set time using the same activation key UP for 3 sec.
The defrost interval depends on the presence of the RTC optional. Ld6, during workdays, and in Sd1…Sd6 during holidays. At the end of defrost dripping time is started, its length is set in the Fdt parameter. An additional parameter FSt provides the setting of temperature, detected by the evaporator probe, above which the fans are always OFF.
This is used to make sure circulation of air only if his temperature is lower than set in FSt. If the difference between the evaporator temperature and the room temperature is higher than the FCt value, the controller will activate the fans.
The on and off interval of time follow the Fon and FoF parameters. When the compressor is stopped the fans will go on working for the Fon time. It will be activated in parallel with the relay of the first compressor, with a possible delay set in the AC1 parameter seconds.
The heating element has to be connected to the oA3 relay If the temperature increases and reaches set point plus differential HY the compressor is started and then turned off when the temperature reaches the set point value again.
If the temperature decreases and reaches the set point minus differential HY the oA3 output heater is switched on and then turned OFF when the temperature reaches again the set point.
DIXELL XR40C CONTROLLER
Emerson Dixell XR60C Installing And Operating Instructions
Dixell XR06CX Operating Manual
Dixell Universal Replacement Controller
- TRAININGSPLAN KRAFTAUSDAUER PDF
- UCF CAMPUS MAP PDF
- ARRIGHI ADAM SMITH IN BEIJING PDF
- COMUNICACIONES DE MARKETING INTEGRADAS DON SCHULTZ PDF
- EREWHON REVISITED PDF
- MEXICO PROFUNDO UNA CIVILIZACION NEGADA PDF
- AJEDREZ PARTIDAS COMENTADAS PDF
- BREAKING GENERATIONAL CURSES & PULLING DOWN STRONGHOLDS PDF
- CHRONOTYPES THE CONSTRUCTION OF TIME PDF